Konros: what are the requirements of ward door
There are different requirements for the use of ward doors in different places.
For the convenience of the access of the hospital bed, the unequal double door is widely used. The vision window of the door is for medical staff to observe the internal situation of the ward at any time to prevent emergencies. Medical door need to be soundproof well, so the selection of sealing materials and sealing technology is worthy of further study. For some radiology department, like CT scan room, the medical door must contain lead plate and well sealed.
In the same way, different materials for ward door the requirements are also different.
The steel door looks simple, but in fact, many manufacturers are difficult to control the molding size of the hospital door, which requires high production technology to ensure the accurate size and product quality.
In order to improve life span of the medical door, it is necessary to do a good job of anti-collision, anti scratch and water-proof performance.
Aluminum alloy edge sealing is added around the door, with aluminum honeycomb inner filling. And stainless steel anti-collision belt is added in the appropriate position, which greatly improves the anti-collision and anti scratch performance. And the door leaf is not easy to deform. At the same time, the aluminum alloy anti-collision clip which is added at the corner of the door frame, plays the same role.
What’s more, the back and bottom of the door are used water-proof technology to improve the moisture resistance.